1, Led separate solar flood light pole bottom diameter, bottom flange plate size should meet the design requirements. In case of special requirements, the manufacturer shall provide detailed drawings of the corresponding products for the consideration of Party A and the design. Solar street light steel material must meet the standard.
2, Led separate solar flood light pole inside and outside should be hot-dip galvanized internal and external surface corrosion treatment process. Galvanized layer should not be too thick, the surface without color difference, rough phenomenon, the above anti-corrosion treatment process should meet the corresponding national standards. Anti-corrosion test report and quality inspection report should be provided during construction.
3, Led separate solar flood light pole surface needs to be color spray treatment, color should be able to meet the requirements of the owner. High grade coating should be used for spraying.
4, Led separate solar flood light pole should be calculated according to the national standard of wind speed, force requirements. During the construction process, the material description and force calculation of the light pole should be provided. For light posts welded with steel ring, the contractor shall clean the welding joints and groove them according to the regulations before welding.
5, Led separate solar flood light pole hand hole door, hand hole door design should be beautiful and generous. The door is plasma cut. The electrical door should be integrated with the rod body, and the structural strength is better. With reasonable operating space, the door with electrical installation accessories. The gap between the door and the rod should be no more than 1 mm and have good waterproof performance. There is a special fastening system, with good anti-theft performance. Electrical doors should have high interchangeability.
6, Led separate solar flood light pole installation should comply with the corresponding national installation procedures and safety regulations in the relevant provisions. Before the installation of the lamp post, appropriate hoisting equipment, lifting point position, displacement and correction method shall be selected according to the height, weight and site conditions of the lamp post, and shall be reported to the supervision engineer for approval; When the lamp post is installed, the two perpendicular directions should be equipped with instruments to check and correct to ensure that the position of the lamp post is correct and the pole body is vertical.
7. When Led separate solar flood light is connected with bolts, the screw should be perpendicular to the penetration surface, there should be no gap between the screw head plane and the member, and each end should not be more than 2 washers. After the bolt is screwed, the length of the exposed nut is not less than two pitch.
8. After the installation and correction of the Led separate solar flood light pole, the Contractor shall immediately backfill and tamp, which shall comply with the relevant regulations.
9, Led separate solar flood light power discharge pipe installation should comply with the drawings and relevant specifications.
10. Led separate solar flood light verticality test: after the lamp pole is upright, use the theodolite to test the verticality between the pole and the horizontal.
11. The overall appearance of the Led separate solar flood light pole: the shape and size meet the requirements, the overall appearance is generous, the rod surface is smooth, and the color is uniform.